Remote terminal with display
Maximum length of pLAN network: 500 m with AWG22 shielded pair cable
PCOC terminal distance: 50 m with telephone cable 500 m with AWG22 shielded pair cable.
Note: to achieve maximum length, use a bus type with distribution lines not exceeding 5 metres.
Clear front cover: clear polycarbonate
Anthracite grey rear casing (wall/recess): polycarbonate + ABS
Keypad: silicone rubber
Clear glass/surround: clear polycarbonate
Self-extinguishing class: V0 at clear front panel and rear casing
HB at silicone keypad and remaining parts.
Power supply from pCO via telephone connector or 18/30 Vdc external source
Protected by external 250 mA fuse
Maximum consumption: 1.2 W.
Use the remote large terminal (code 28154171) as the main display for the PCOC Regulator for the external user terminal (code 28154132). There is always the option of using two terminals as displays. For this purpose, use the PCOC Regulator as the user terminal (code 28154142) together with the remote terminal (code 28154171). This allows to view and control the system both from the regulator and the terminal (both with displays).
Inclusive of frame for large terminal.